Question about Fahrenheat Electric Convector Baseboard Heater, 240 Volt
I have 3 baseboard heaters in series (one wire for all with a thermostat on the first of them which therefore controls power to all three). Problem is the thermostat acts like a rheostat and appears to be reducing power to the second and third heater (which do warm but only slightly). Do I need a different, high-duty thermostat?
The heaters need to be wired in parallel so they all receive the same voltage. If wired in series the first heater will receive proper voltage and the next heater will receive reduced voltage (Voltage Drop across first heater) and so on (Ohm's Law). You may want to have an electrician help you so you don't get electrocuted or burn up your heaters or your house. Hope this helps!
Posted on Dec 10, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Apr 12, 2013 | Honeywell Heating & Cooling
Feb 14, 2011 | Fahrenheat F2545 Electric Baseboard Heater
Nov 04, 2010 | Fahrenheat Electric Convector Baseboard...
Dec 26, 2008 | Fahrenheat Electric Convector Baseboard...
Dec 14, 2008 | Fahrenheat Electric Convector Baseboard...
Oct 20, 2008 | Fahrenheat Electric Convector Baseboard...
Mar 17, 2008 | Fahrenheat Electric Convector Baseboard...
Nov 28, 2007 | Fahrenheat Electric Convector Baseboard...
173 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: