Question about York Yankees Bedding MLB Comforter
I have a York heat pump Model # E2EBQ24AQ6A.
Recently I have installed a Forced Air 2 stage heating Gas furnace in my house and I don't want to use heating from heat pump. Just I want to use A/C. Could you please let me know how I can do the wiring for the heat pump to the furnace circuit board. The thermostat wires are already hooked up to the furnace and its working. R,G,W.
Thank you for your time.
Yes i can , you need to hookup the r and the o together so that the reversing vvalvce is allways energized . so with that im mind send r,y,c,o to theout side unit. at the ahu you'll hook up the 5 wires for the furnace, r g w1 w2 com and at the thermostat r,w1,w2,y,g,com,o then you will be set (the o get hooked up to o and goes straight out side.
Posted on Dec 25, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Feb 02, 2016 | Heating & Cooling
Nov 23, 2013 | Source1 CTS Series Model S1-THPU32P7S...
Mar 01, 2011 | Bryant Heating & Cooling
Jun 27, 2010 | Heating & Cooling
Mar 07, 2010 | Heating & Cooling
Jan 03, 2010 | Heating & Cooling
Nov 14, 2009 | Honeywell Programmable Thermostat Heater
May 07, 2009 | Heating & Cooling
Jan 17, 2009 | Honeywell Programmable Thermostat Heater
Jul 03, 2008 | Heating & Cooling
1,023 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: