Question about Carrier Heating & Cooling
The e2 code on a carrier comfort zone thermostat is indicitive of the external safety sensors which are located on your units ductwork in the attic. the e2 code are the hpt/ and lat sensor codes. the hpt is the heat pump temperature sensor and the lat is the leaving air temperature sensor. you can pull off the cover of the panel and behind it will actually give you all the fault codes associated with you carrier tsat.each sensor has a certain ohm rating and if its out of the range it will fail. now as to the reasons for failure, the indoor coil could be dirty, filters dirty, refrigerant charge incorrect.
Posted on Dec 22, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Mar 25, 2015 | Carrier Heating & Cooling
on Mar 02, 2008 | Carrier XHB123D X/Y Series Heat/Cool Air...
Jul 06, 2011 | Dometic Rooftop RV Air Conditioner
Jan 03, 2010 | Heating & Cooling
Nov 22, 2009 | Carrier TSTATHCP Programmable Thermostat...
Jun 29, 2009 | Carrier 38CKC060 Air Conditioner
Jun 13, 2009 | Heating & Cooling
Jan 25, 2009 | Carrier Heating & Cooling
1,898 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: