Question about Mitsubishi MS12TN Air Conditioner
I have a wall mounted unit in my office that runs well for half hour then stops, the operation light flashes once this happens and there is no airflow, ive had an engineer look at it and he said when he put the gauges on it ( the outdoor unit)was running at 8 bar on the low side and was running at 8 bar but the high pressure side would get up to a very high pressure but then it cuts out,any ideas please?!?
This can happen in cold humid weather, when you use heating mode and the outside unit freezes up. All my split-type airconditioners do that occasionally when the weather is like that. The inside fan stops for some 10 minutes with light flashing, then it picks up again after the outside unit warmed up.
Posted on Jan 09, 2008
Hello, It depends what refrigerant the system is on but if it tripping out on HP it could be overcharged with gas or a problem with the outside condesor fan.
Posted on Feb 15, 2007
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Aug 19, 2016 | Carrier Heating & Cooling
Mar 11, 2015 | Daikin FTXS18HVJU Wall Mounted Indoor Unit...
Jan 02, 2014 | LG LS-K2430HL Heat Cool Mini Split Air...
Apr 13, 2013 | Heating & Cooling
Jan 30, 2012 | Fujitsu 24C1 Air Conditioner
Jun 11, 2011 | Sears Craftsman LiftMaster Chamberlain...
Jan 08, 2011 | Heating & Cooling
Mar 13, 2008 | Creative Labs ZEN Vision:M Digital Media...
Nov 19, 2013 | Mitsubishi MS12TN Air Conditioner
Sep 29, 2012 | Mitsubishi MS12TN Air Conditioner
423 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: