Question about Dayton Heating & Cooling
The fan runs fine but the burners never light.
Check your thermostat and see that it’s wired correctly, it should be as followed for this particular unit; R-W-G from the thermostat terminal, and R-W1-G on the units terminal strip. Also check and make sure you have gas to the unit and make sure the switch to the gas valve is in the “ON” position. If all of the above is correct and working, you could have a bad igniter, or a have a flame rollout, or high limit switch tripped.
Hope this helps
Posted on Dec 03, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Nov 24, 2012 | Dayton Gas Furnace Heater
Nov 13, 2011 | Dayton Heating & Cooling
Feb 06, 2011 | Dayton (3E379) Heater
Nov 13, 2010 | Dayton Gas Furnace Heater
Feb 09, 2010 | Dayton (3E379) Heater
Feb 24, 2009 | Dayton (4LX41) Heater
Nov 20, 2008 | Dayton (3E379) Heater
Dec 30, 2007 | Heating & Cooling
174 people viewed this question
Usually answered in minutes!