Question about Honeywell HE360A1027 Whole House Humidifier Humidifier
When the furnace comes on the humidistat turns the humidifier on a few sceonds later, but no water gets to the Humidifier pad. I unscrewed the water supply to the selenoid and a strong stream of water came out so I know I'm getting water to the selenoid. Could I have a bad selenoid? If so, do you know where I could get a new one?
Try to clear the small pinhole in the fitting leading into the selenoid. Sometimes this gets blocked with dirt or sand.
Posted on Dec 26, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Nov 13, 2010 | Aprilaire 700 Humidifier
Mar 03, 2010 | Aprilaire 700 Humidifier
Mar 03, 2010 | Aprilaire 600 Humidifier
Dec 28, 2009 | Honeywell HE260A1010 Whole House...
Nov 28, 2009 | Honeywell HE260A1010 Whole House...
Mar 04, 2009 | AutoFlo 400BP Humidifier
Feb 01, 2009 | Honeywell HE360A1027 Whole House...
Jan 28, 2009 | Aprilaire 700 Humidifier
Jan 09, 2014 | Honeywell HE360A1027 Whole House...
140 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: