Question about Aprilaire 600 Humidifier
I have wired up the Aprilaire 700 and when I turn it up to 5 when the furnace is running, it shuts the furnace off, when I turn it down the furnace comes back on....
It is possible you may have wired it wrong. Make sure your humidifer is not robbing power from your thermostat. This would explain when your humidifer makes a demand to come on it robs power from your t-stat making it lose its call for heat. Wire your humidistat to the "w" terminal and the common terminal so it only runs on a call for heat. With the bypass type of humidifier you purchased it wont do you any good to run when the heat isn't running anyway. If you want an independent operation humidifier you need a steam type.
Posted on Jan 05, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Nov 16, 2012 | Aprilaire 700 Humidifier
Jan 08, 2010 | Aprilaire 600 Humidifier
Jan 01, 2010 | Aprilaire 700 Humidifier
Dec 11, 2009 | Aprilaire 700 Humidifier
Feb 06, 2009 | Aprilaire 700 Humidifier
Jan 25, 2009 | Aprilaire 700 Humidifier
May 22, 2017 | Aprilaire 600 Humidifier
149 people viewed this question
Usually answered in minutes!