Question about Heating & Cooling
SOURCE: ferroli optimax 31c
Here is a link to the manual.It shows fault codes.
Please rate this solution.
Posted on Jan 17, 2009
D2 is not a fault what that means is delay and 2 refers to CH which means the boiler has gone into standby mode. you need to check that your CH circut is open, there is a filter on the return valve into boiler make sure this is not blocked. If this is blocked the water is just going though the boiler by-pass so then the boiler thinks its up to temp. hope this helps
Posted on May 04, 2010
Tips for a great answer:
Mar 24, 2013 | Quasar HQ2051TH Air Conditioner
May 03, 2012 | Heating & Cooling
Dec 22, 2010 | Heating & Cooling
Dec 18, 2010 | Heating & Cooling
Sep 26, 2010 | Quasar HQ2051TH Air Conditioner
Oct 07, 2009 | Comfort-Aire RAD-243 Air Conditioner
Mar 28, 2009 | Quasar HQ2051TH Air Conditioner
Jan 16, 2009 | Heating & Cooling
91 people viewed this question
Usually answered in minutes!