Question about Heating & Cooling
Check your TXV outside just like you do inside. Strap temperature sensor to outlet of TXV, disconnect the bulb.and let run 5 min, Get temperature reading, then put the bulb in your hand and watch the bulb open up. Next stick in a cup of ice water and watch close.
Check your 4 way valve for proper operation.
Do not hit accept unless you can give 100% good feed back.
If you need more help Please post back.
Let me know how it went.
Posted on Dec 01, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Mar 07, 2016 | Heating & Cooling
Jun 20, 2015 | Ruud Heating & Cooling
Feb 06, 2011 | Ruud Heating & Cooling
Apr 19, 2009 | Ruud UBHC Air Conditioner
Feb 03, 2009 | Ruud Central System Air Conditioner
Oct 20, 2008 | Heating & Cooling
Jun 06, 2008 | Ruud UBHC Air Conditioner
181 people viewed this question
Usually answered in minutes!