Question about Goodman Air Conditioners
This from the installation manual on your furnace.
I think you need check the flame senor for proper output. if the output is correct you wil have to switch the electronic board.
FLAME SENSOR (QUALIFIED SERVICER ONLY)
Under some conditions, the fuel or air supply can create a nearly
invisible coating on the flame sensor. This coating acts as an
insulator causing a drop in the flame sense signal. If the flame
sense signal drops too low the furnace will not sense flame and
will lock out. The flame sensor should be carefully cleaned by a
qualified servicer using emery cloth or steel wool. Following cleaning,
the flame sense signal should be 1 to 6 microamps at 115
Post me back and let me know.
Posted on Dec 01, 2008
Tips for a great answer:
Sep 10, 2011 | Air Conditioners
Jun 22, 2011 | Air Conditioners
May 16, 2011 | Air Conditioners
Feb 20, 2011 | Air Conditioners
Dec 27, 2010 | Air Conditioners
Nov 27, 2010 | Air Conditioners
Nov 24, 2010 | Air Conditioners
Dec 05, 2008 | Air Conditioners
Sep 17, 2008 | Intertherm Air Conditioners
284 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: