Question about Goodman Heating & Cooling
This from the installation manual on your furnace.
I think you need check the flame senor for proper output. if the output is correct you wil have to switch the electronic board.
FLAME SENSOR (QUALIFIED SERVICER ONLY)
Under some conditions, the fuel or air supply can create a nearly
invisible coating on the flame sensor. This coating acts as an
insulator causing a drop in the flame sense signal. If the flame
sense signal drops too low the furnace will not sense flame and
will lock out. The flame sensor should be carefully cleaned by a
qualified servicer using emery cloth or steel wool. Following cleaning,
the flame sense signal should be 1 to 6 microamps at 115
Post me back and let me know.
Posted on Dec 01, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Sep 10, 2011 | Heating & Cooling
Jun 22, 2011 | Heating & Cooling
May 16, 2011 | Heating & Cooling
Feb 20, 2011 | Heating & Cooling
Dec 27, 2010 | Heating & Cooling
Nov 27, 2010 | Heating & Cooling
Nov 24, 2010 | Heating & Cooling
Dec 05, 2008 | Heating & Cooling
Sep 17, 2008 | Intertherm Heating & Cooling
285 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: