Question about Honeywell Heating & Cooling
That particular intermittent pilot gas valve uses one of three ignition control modules; S86F, S8600F, and S8610. Check the pilot assembly and look at the flame, could be a weak flame, dirty or clogged, if its not lit or weak, you’ll hear a constant buzzing or “sparking” sound, this will lock-out the gas valve. If you hear nothing at all, start with cleaning or replacing the pilot assembly, then check the ignition control module.
Hope this helps
Posted on Dec 03, 2008
Wiggle wires, it could be something as simple as a loos connection. If your getting power to valve and it's not opening your valve is bad. Also check your limits somethimes all limits are connected and one broken one will throw the system off.
Posted on Dec 02, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Oct 07, 2013 | Goodman GMS807034ANA Heater
Jul 23, 2011 | Dryers
Jan 26, 2011 | Coleman Propane Forced Air Heater...
Dec 15, 2010 | Heating & Cooling
Nov 28, 2010 | Ruud UBHC Air Conditioner
Nov 07, 2010 | Dryers
Dec 23, 2009 | Hotpoint RGB790SEHSA Gas Kitchen Range
Dec 11, 2008 | Goodman GDS80904BNA Open Flame Heater
May 24, 2017 | Honeywell Heating & Cooling
234 people viewed this question
Usually answered in minutes!