Question about True Food VWR Storage Refrigerators with Stainless Steel Doors, 1 to 4°C T72NCVWR w/ FREE UPS
With the refrigerator, the fan inside the conditioned space should always run. This is normal for most all commercial refrigerators. Need to check to see if the unit is shutting off the compressor after the conditioned space reaches a good temp, usually 35 degrees. If not, probably a bad thermostat.
Posted on Jul 28, 2017
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
If its getting warmer or more humid where you are this is probably a
sign of needing to clean your outer coils. Remove the panel covering
the compressor and check the condition of the coils. Clean with a nylon
brush or wire brush. Or blow out with compressed air.
If the outer coils look OK see if they feel warm up and down the sides. If they don't you may have a defrost problem. If they are warm recheck them in 30 minutes if still warm or warmer and no one has opened the door check the lite inside, and the fan inside (it will only run with door closed). Hit the switch and see if lite goes out and make sure the switch is being activated with the door closed. And check the door seals any vinyl cracked on them they need replacing but can be warped sometimes letting in warm air (usually a sign of frost inside the door or water leaking out but not always).
It could be low on refrigerant or an inefficient compressor but not likely as much as these other items are.
The last thing is the thermometer could be reading wrong or out of calibration. Is it Electronic? Yes - Then its most likely one of the other problem before. If its mechanical (bi-metal) get another thermometer you trust or a new one and check it before you trust it. 2 of them telling you its 5'f then Id believe it other wise one or both of them are wrong.
Posted on Mar 12, 2009
SOURCE: commercial TRUE GDM soda machine
If the cooler has power, the condesor fan (bottom) and evaporator fan (top) are spinning put your hand on the compressor. Do you feel a vibration? if so, you probably have a refrigerant leak. If not (if its clicking or nothing at all) its a compressor issue.
Posted on Aug 13, 2009
If you can gain access to the compressor, you will see 2 copper lines going to the compressor. One is smaller than the other. VERY CAREFULLY lightly touch the smaller line while the unit is running. If the compressor is running, that line will be extremely hot.
Let me know if I can be of further help.
Posted on Jun 29, 2010
Tips for a great answer:
Apr 02, 2014 | True TSD-33G Stainless Steel Cooler...
May 09, 2011 | Maytag MFI2568AES Stainless Steel Bottom...
Sep 16, 2010 | Liebherr KBES3650 Stainless Steel...
Dec 24, 2009 | Refrigerators
May 18, 2008 | LG (LRBC22522ST) Stainless Steel
Mar 30, 2008 | GE PFS22SBSSS Stainless Steel French Door...
94 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: