Question about Heating & Cooling
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
SOURCE: Boiler won't start
near one corner of the gas valve is a slottedplug.
It looks like large screw headremove the plug just like any screw. This lets you access the gas pressure adjustment screw.
Usually no more than one half to one full turn is needed. (clockwise to increase pressure)
It is important that you not have to much Gas pressure as this will cause overheating and premature heat exchanger failure.
The best thing to do is check the pressure going into the gas valve, and also coming out. Make sure the inlet side of the GV is not partially clogged where the pipe comes in. (especially if you have copper pipe with natural gas)
Posted on Jan 10, 2009
SOURCE: Carrier furnace
I'm not a fan of zoning but it sounds like they don't have the ducting done correctly. There has to be bleeder trunks installed in the unit because your are taking a unit that is designed to cool or heat a particular square footage and make it cool or heat a smaller area. This makes the unit way too big for the job you are asking it to do. If the ducting is improper, you are going to have issues like this. A lot of contractors will not admit that the ducting isn't correct due to the cost to correct it. I personally think (my opinion) that 4 zones are a little excessive. Sounds like you really need 2 units. It's hard to tell from my point of view since I'm not there to actually see what is going on. I would have a couple of different contractors come out and give you an estimate to fix the issue and then tell the installer to come and fix what they say is wrong.
Posted on Mar 16, 2009
Between the burners is a small rail in the pressed steel where the flame runs across to light the other burners and it sounds like there is dirt or debris in the step over rails causing the problem. You will need to use some compressed air on those rails to clear them out. Once the rails are clear the other two burners should ignite right away.
Posted on Dec 21, 2009
Testimonial: "I did not expect such a quick response. These are hard times for us and we really appreciate your help. Thankyou for sharing your expertise."
what kind of split system do you have is it a ductless split like shown or do you have actual duct work where you can change the dampers
Posted on Sep 19, 2010
Tips for a great answer:
Dec 05, 2016 | Heating & Cooling
Nov 04, 2014 | Amtrol WHS-80Z - WHS-80Z 80Gal Hot Wtr...
Mar 01, 2014 | Weil-McLain CGa-25-SPDN, NG, Gas Fired...
Dec 07, 2017 | Heating & Cooling
Dec 17, 2013 | Heating & Cooling
Nov 06, 2012 | Heating & Cooling
Sep 20, 2010 | Honeywell (CT62B1015) Baseboard Heater
Jan 16, 2009 | Honeywell Programmable Thermostat Heater
Jan 07, 2009 | Honeywell Electronic Programmable...
Apr 21, 2018 | LG Heating & Cooling
60 people viewed this question
Usually answered in minutes!