Question about Hitachi RAS-09UH Air Conditioner
Hi my aircon light keeps flashing off amd on and thats all it does it was fine untill i took it down from my shop and then 2 weeks later insatlled it in my house all the wiring is installed correctly could it be that the gas leaked all out when i took the pipes off
Before you disconnected you should have pumped the system down, keeping all of the gas in to the outdoor unit. when you reinstalled you needed to vac the pipework then open the outdoor unit valves to let the refrigerant through. if you had disconnected the pipework without doing this you would have lost the gas, so yes a recharge will be required. hope this helps.
Posted on Mar 04, 2007
Tips for a great answer:
Apr 06, 2016 | LG LSC121PMA Split System Air Conditioner
Apr 10, 2014 | Air Conditioners
Jan 18, 2013 | LG LSC121PMA Split System Air Conditioner
Feb 03, 2011 | Air Conditioners
Dec 12, 2010 | Air Conditioners
Apr 29, 2010 | LG Art Cool LA181CNW Split System Air...
Jan 19, 2010 | Air Conditioners
May 04, 2014 | Hitachi RAS-09UH Air Conditioner
118 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: