Question about Coleman Propane Forced Air Heater w/Electronic Ignition (50,000-80,000 BTU)
The furnace ignition glows and ignites and as soon as the blower comes on the flames goes out a few seconds later the thing glows again and it lights only to go out again when the furnace blower stops the green light blinking once indicating ignition failure can you help with any suggestions
Sounding like a flame proving device is failing to sense flame. Try to clean the device with some steel wool. It is located right next to the last burner looks like a thick wire. Take the steel wool and gently rub the carbon that has built up off. Should only take 4 or 5 strokes. Let me know it that did it. Ken
Posted on Dec 02, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Oct 26, 2013 | Gibson KG7TC060D24B 60,000 BTU 95.1% Gas...
Feb 10, 2011 | Coleman Heating & Cooling
Jan 22, 2011 | Heating & Cooling
Dec 26, 2009 | Tools & Hardware - Others
Nov 23, 2009 | Heating & Cooling
Oct 20, 2009 | Ruud UBHC Air Conditioner
Oct 03, 2009 | Maytag Neptune MDG5500AW Gas Dryer
Oct 01, 2008 | Goodman GDS80904BNA Open Flame Heater
May 15, 2014 | Coleman Propane Forced Air Heater...
491 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: