Question about Heating & Cooling
If your igniter comes on but no ignition, that eliminates the possibility of a bad or clogged pressure switch, high limit or flame rollout switch. Sounds to me like you have a control board, or a gas valve going bad. Could even be some loose, corroded, or faulty wiring. Before the igniter comes on the furnace does a self diagnostics to ensure everything is working, or the furnace will not make it to the igniter sequence. Inducer motor, pressure switch/s, limit controls are closed…then comes on the ignitier, gas valve opens, pilot runners and burners ignite, flame sensor detects the flame, blower comes on and all operations are working.
Hope this helps
Posted on Dec 02, 2008
a 6ya Repairman can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repair professionals here in the US.
click here to Talk to a Repairman (only for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jan 11, 2013 | Water Heaters
Dec 21, 2010 | Reddy R70ET Utility Heater
Here are a couple of tips that I wrote that tell you how to troubleshoot a Torpedo or Reddy heater...
Reddy Heater - Troubleshooting Torpedo Heaters
Dec 12, 2010 | Reddy Heater-30-55,000 BTU Variable
Oct 17, 2009 | Pool & Spa
Feb 11, 2009 | Amana ARGS7650SS Gas Kitchen Range
Dec 10, 2008 | Goodman GMS90703BXA Heater
Nov 21, 2008 | Heating & Cooling
May 22, 2008 | Kenmore 74602 Gas Dryer
Dec 04, 2007 | Reddy Heater-30-55,000 BTU Variable
340 people viewed this question
Usually answered in minutes!