Question about Honeywell Heating & Cooling
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
SOURCE: contour comfort control
normally, if you have a hold option, there should be a hold button which when you press again should un hold the setting. have you tried pressing the run button. this would eliminate all hold function and just run the programmed temperatures.
Posted on Feb 17, 2008
Q1# do you have printer driver? what kind of driver ur using? is your driver from www.zebra.com?
Q2#what software u are using to print?
Q3#ask the programmer of the software if there is a command that control the settings of the printer
Q4# is the software DOS or windows program
Posted on Mar 20, 2009
press run program.... from there, set the schedule for maximum efficiency. permanent hold only shows up after the hold button has been pressed 2-3 times. If this does not fix the issue, there is a master reset button on the thermostat that will set all settings back to factory default.
Posted on May 17, 2009
SOURCE: Honeywell TH8320U1008
simply push cancel. That clears the hold feature.
Pushing hold once gets - permanent hold.
Pushing hold twice gets - days of permanent hold. So you can set it if you are going away on a temp and at the end of the days it goes back to normal operation.
Posted on Jul 23, 2009
How old is your system?
If your system is a heat pump and is failing to keep up overnight during the colder weather. Or if it struggles to keep up at all, a few issues come to mind.
Obviously, the first and most common cause would be due to an undercharge of refrigerant. With an undercharge, your heat pump has lost efficiency and cannot properly remove heat from outside.
Other possible issues that come to mind are failed defrost cycle. If your unit is not defrosting properly and it continues to run non-stop, a freeze-up could occur on the outdoor coil. And the worse it gets, the worse your system will perform.
Another possibility is auxiliary heat or heat strips are not coming on at all. Depending on your thermostat, you would be able to tell if the thermostat is calling for auxiliary heat. If you are not getting any additional heat, then the heat pump may not be adequate for the space intended.
Other smaller factors may come into play such as incorrect defrost cycles. Possibly a mechanical component taking a break or overheating or maybe a mechanical failure such as failed compressor leaving the only heat you have as emergency.
Posted on Jan 09, 2010
Tips for a great answer:
Jun 21, 2017 | Heating & Cooling
Oct 21, 2017 | Heating & Cooling
Oct 08, 2014 | Heating & Cooling
Mar 12, 2017 | Heating & Cooling
Jun 30, 2011 | Heating & Cooling
Nov 15, 2010 | Heating & Cooling
Feb 06, 2010 | White Rodgers White-Rodgers 1F85RF-275...
Sep 13, 2009 | Honeywell Programmable Thermostat Heater
May 12, 2017 | Honeywell Heating & Cooling
Nov 25, 2008 | Heating & Cooling
54 people viewed this question
Usually answered in minutes!