Question about Heating & Cooling
It starts for about 2 seconds, then starts again for about 2 seconds, then shuts off. After about the 3rd time it tries to start, the furnace makes a thump sound and blower kicks in and runs for about 15-20 seconds and then completely stops.
First let me thank all the pros that take the time to answer our questions. My wife thinks I'm a genious. I had the same problem up to 30 minutes ago and fixed it from a solution found on a different webpage. There's sensor sticking up where the flames come out with a single wire coming from it. Remove the sensor and scrub it with steel wool. Replace it and get your hummer from the old lady because you just saved her a few hundred bucks.
Posted on Jan 17, 2012
The reason why it stops and starts is that the sensor within the burner can not sense a flame in the furnace. The parts need to checked is the fuel filter, Air in the line, burnt out arcing rods or a bad ac high voltage transformer.
Posted on Nov 30, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jan 06, 2017 | Heating & Cooling
Jan 03, 2017 | Royal Heating & Cooling
Dec 31, 2016 | Heating & Cooling
Jan 25, 2015 | Heating & Cooling
Dec 25, 2014 | Heating & Cooling
Nov 11, 2014 | Heating & Cooling
Nov 07, 2014 | Heating & Cooling
Nov 28, 2013 | Heating & Cooling
4,491 people viewed this question
Usually answered in minutes!