Question about Heating & Cooling
The simple diagram for that specific problem it connected series to thermal cut off sensor.
The two black wires, One came from a power supply line (it means an active power
and the other one goes to the load motor) If you shorted it connection it will run the motor.
But it bypass the sensor.
Unplug the power then try to fix the both end of that black wire connected to terminal bolt of your thermal sensor by replacing the broken plastic nut with a new one.
Fit the nut thight to avoid electrical arch while giving power on at the start.
Posted on Nov 29, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Oct 08, 2012 | Intertherm Heating Cooling System 15kw...
Oct 08, 2012 | Honeywell Icp Heil Tempstar Furnace Spark...
Jan 02, 2011 | Weather King Heating & Cooling
Oct 07, 2010 | Heating & Cooling
Jan 20, 2010 | Ruud UBHC Air Conditioner
Dec 25, 2009 | Ruud UBHC Air Conditioner
Dec 09, 2009 | Ruud Heating & Cooling
Sep 24, 2008 | Heating & Cooling
May 02, 2008 | Heating & Cooling
71 people viewed this question
Usually answered in minutes!