Question about Heating & Cooling
The movement of the diverter valve is critical on this appliance, and is located on rear right of the boiler, when hot water is turned on, theres are two microswitches, which must break (they both close in Central heating mode), if pump is running, it is recognising the hot water demand, check microswitches are breaking, if not, it tends to be a defective servo valve (located above the water valve), or a blocked/ restricted control line (small copper tubes which connect into the servo valve)
Posted on Mar 03, 2009
Drips of water obviously indicate a leak - locate the leak - althought it could be condensation unlikely & that would be in more than one place around the boiler.
obviously as it may sound - is the gas meter is a pre-paid one - check there is plenty of credit & the meter is ON and not on emergency credit
boilers are like women - not always easy to figure out and why they suddenly go wrong when all has been well !
leaks mean bar pressure dropping - so check for leaks and check if water is leaking from the pipe on the outside wall - problem could be with the Pressure Relief Value (PRV) not working properly - hence not allowing the system to maintain pressure and releasing it - so check bar pressure
possible problem with expansion tank?
or Printed Circuit Board - so check by topping up the system - by turning on top up tap - see if the bar pressure will go up to maximum - if it does close top up tap before maximum bar 3.5 - see if any water leaks outside - if so - monitor the pressure gauage and turn on the hot taps full
the the gas burner lights up - some progress - atleast the gas value isnt at fault necessarily - if the burner stays on for a while at least 10-15mins - then atleast it's ok to assume the heat sensors, the heat exchanger and gas value are ok. -
now see if the bar pressures is falling - if it is - then probs with PRV - probably needs replacing.
these boilers are OLD however i have found them to be very reliable - there are newer more efficient ones on the markert but why replace an entire boiler if it;'s been very reliable ?
there is a temporarily solution around the PRV and that's to leave the top up tap partially on - the water may not get as hot but hot enough and your outside wall will get very wet until an engineer visits - good luck but get a professional in.
- if it's falling there's an indicator it's the PRV -
Posted on Jan 06, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Oct 27, 2014 | Water Heaters
Oct 22, 2014 | Water Heaters
Oct 03, 2013 | Heating & Cooling
Nov 11, 2012 | Computers & Internet
Feb 23, 2010 | KDS Valiant 6380iPTD-01 Notebook
Dec 21, 2009 | Water Heaters
Oct 12, 2009 | Water Heaters
Sep 21, 2009 | Heating & Cooling
Aug 31, 2009 | Water Heaters
Mar 25, 2009 | Water Heaters
Apr 28, 2017 | GE Heating & Cooling
Apr 28, 2017 | Dimplex Heating & Cooling
1,984 people viewed this question
Usually answered in minutes!