Question about Carrier Heating & Cooling
Carrier time delay relay can be replaced by generic icm time delay 5 minute delay on break or a new digital stat that has a 5 min time delay built in. simply break the yellow wire through the low voltage at the condensor. usually a common and a yellow in and a yellow out are connected to the old relay. sometimes a red as well. the old relays needed power and a common all the time and a yellow in when contactor call is sent and a yellow out to the contactor after delay times out. new two wire delays only need power in and power out. they have a dial to adjust desired delay 0 to 5 minutes. good luck good luck
Posted on Dec 07, 2008
I looked up information and the unit is obsolete. I also did not see a time delay in the diagram with the original unit. It must have been added later. Post me back and let me know where it goes and what numbers it has on it.
Posted on Dec 01, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Dec 07, 2014 | Bryant Heating & Cooling
Sep 15, 2013 | Intertherm P3RA-042K Air Conditioner
Jun 15, 2011 | Carrier Heating & Cooling
Jul 24, 2009 | Heating & Cooling
Jul 12, 2009 | Heating & Cooling
May 12, 2009 | Heating & Cooling
Mar 10, 2009 | Carrier XHB123D X/Y Series Heat/Cool Air...
Jan 16, 2009 | Goodman PHKJ048-1 Air Conditioner
Jun 27, 2008 | Carrier 38CKC042 Air Conditioner
Jun 25, 2008 | Carrier 38CKC042 Air Conditioner
134 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: