Question about Carrier Heating & Cooling
Carrier time delay relay can be replaced by generic icm time delay 5 minute delay on break or a new digital stat that has a 5 min time delay built in. simply break the yellow wire through the low voltage at the condensor. usually a common and a yellow in and a yellow out are connected to the old relay. sometimes a red as well. the old relays needed power and a common all the time and a yellow in when contactor call is sent and a yellow out to the contactor after delay times out. new two wire delays only need power in and power out. they have a dial to adjust desired delay 0 to 5 minutes. good luck good luck
Posted on Dec 07, 2008
I looked up information and the unit is obsolete. I also did not see a time delay in the diagram with the original unit. It must have been added later. Post me back and let me know where it goes and what numbers it has on it.
Posted on Dec 01, 2008
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Tips for a great answer:
Dec 07, 2014 | Bryant Heating & Cooling
Aug 15, 2011 | Amperite Dayton Solid State Timer On Delay...
Apr 04, 2011 | Amperite Dayton Solid State Timer On Delay...
Feb 03, 2011 | Amperite Dayton Solid State Timer On Delay...
Jan 06, 2011 | Amperite Dayton Solid State Timer On Delay...
Mar 10, 2009 | Carrier XHB123D X/Y Series Heat/Cool Air...
Aug 31, 2008 | Kenmore 16602 / 16604 / 16609 Built-in...
Jun 27, 2008 | Carrier 38CKC042 Air Conditioner
135 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: