Question about GE Zoneline AZ55H07D Air Conditioner
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
SOURCE: Zoneline PTAC short circuit
Most likely you will need to either replace transformer or there may be a low voltage flat type "car fuse" usually 3 amp or 5 amp for just such an occasion. Good luck!
Posted on Mar 30, 2008
I would go back to person who gave that advice because just the right touch on that capacitor and YOU my friend will be in the hospital. If this is helpful, please post as such. TY
Posted on Jan 17, 2009
you could have a relay or contactor inside the unit welded closed, therefore compressor will keep operating when unit is off. replace compressor contactor.
Posted on Feb 10, 2009
Most of the cases when tou heard a click on and off is aproblem with the compresor that goes off on overload, when the compresor try to start and is stuck , burned or the starting coil inside it is open it's overheat and goes off by the thermo bimetal switch.Also could be the capacitor, to check it you need a capacitor tester,but if you don't have it you can try to put anew one (no more than 10 $) and see what happend if still the compresor is getting hot and won't turn on it's burned, jamed or open , and you have to replce it ,if it's less than a year old it should be under warranty but if not is an expensive job and you better get a new unit.
Posted on Apr 15, 2009
Tips for a great answer:
Jul 14, 2015 | Maytag Heating & Cooling
Jul 22, 2008 | GE Heating & Cooling
Jun 01, 2015 | GE Zoneline In Wall Ptac Unit Air...
Jun 07, 2013 | GE Zoneline AZ55H07D Air Conditioner
Sep 07, 2009 | Heating & Cooling
Jul 05, 2009 | GE Quiet-Aire Ductless Split System Air...
Apr 14, 2009 | Fedders A7DH45B2A Dehumidifier
Dec 19, 2008 | Heating & Cooling
Jul 18, 2008 | Carrier 38CKC036 Air Conditioner
247 people viewed this question
Usually answered in minutes!