Question about Weather King Heating & Cooling
Follow the wires back from the motor to either the relay or the circuit board. normally a furnace has a board. check to see if there is any power leaving relay/board to the mtr. if it is a furnace you may need to push in the door saftey switch to get power to system. heat pump mtrs need 230 vlts furnaces 115vlts. If the power is going through to mtr properly than problem is either capacitor or mtr. capacitor can be checked for you by a local hvac supplier or buy a meter that can check it.
PLEASE rate or solution thanks. Brian S.
Posted on Nov 28, 2008
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Dec 16, 2015 | 1990 Ford Tempo
Feb 20, 2013 | 2003 Dodge Durango
Aug 03, 2012 | 1990 Buick Century
May 09, 2011 | 1999 Plymouth Breeze
Mar 05, 2010 | 1991 Oldsmobile Ninety Eight Regency
Jan 09, 2009 | 2000 GMC Safari
Dec 27, 2008 | 1996 Chevrolet K1500
Jul 07, 2008 | 2000 Ford Focus
133 people viewed this question
Usually answered in minutes!