Question about Honeywell CT87B ROUND HEATING&COOLING MECHANICAL THERMOSTAT - WHITE Heater
Your problem may be at the furnace control end and not your thermostat. To determine that, simply unhook the two wires from your thermostat so that they do not make contact. When they are electrically opened like that, your furnace should shut down. If it doesn't, then the problem is at the furnace control board. You may have a relay that is staying on even when power to it is disabled.
Hope that helps...
Posted on Nov 28, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Aug 10, 2014 | Honeywell Heating & Cooling
Oct 24, 2009 | Honeywell Electronic Programmable...
Apr 05, 2009 | Honeywell Programmable Thermostat Heater
Jan 31, 2009 | Honeywell Programmable Thermostat Heater
Jan 05, 2009 | Honeywell Programmable Thermostat Heater
Nov 24, 2008 | Honeywell Electronic Programmable...
Oct 16, 2007 | Honeywell Programmable Thermostat Heater
Dec 01, 2013 | Honeywell CT87B ROUND HEATING&COOLING...
174 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: