Question about Empire GWT-25 Wall Mounted Panel Heater
Year worked fine 4 days until gas co. added additional tank yesterday and now won't stay lit for very long. Relit 5-6 times over evening and got up in night 2x to relight. Stll out again in am. Was able to visually inspect in daylight (T-Day) no obvious issues- vent appears clear tanks look fine. Anything else to look at? Can't get tech help til tomorrow with holiday- do have back-up electric heat.........Thanks!
There could be something stuck in the pilot assembly since you added a new tank to system. Check to make sure flame is hitting thermalcouple. Can you wait for a repair man to come and take pilot assembly out and clean. He will also replace thermalcouple. If you can't wait and you feel comfortable with taking pilot assembly out. Turn gas and electric off to unit then pull cover panel off. Pilot assembly is held in with two screws. Take tube off of gas valve and take off thermalcouple line off gas valve too. take out pilot assebly. Once you have it out take gas line off bottom of pilot assembly. There is a orfice in side make sure you can see through the orfice. You can also clean thermalcouple with a wire brush or sand papper. Reinstall pilot assembly make sure all fittings are tight. turn gas back on and light pilot. If everything looks good turn power on. Turn heat up run heater for a few minutes then turn heater down and let sit to see if it will stay on.
Posted on Nov 29, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Dec 08, 2015 | Williams Heating & Cooling
Nov 05, 2014 | Leisure HOMEPRIDE Electric Fireplace...
Jan 22, 2011 | Honeywell HZ-709 Oil Filled Radiator...
Jan 05, 2011 | Heating & Cooling
Oct 26, 2009 | All-Pro Propane Garage Shop Heaters - All...
Dec 02, 2008 | Reddy Heater RLP100 Portable Forced Air...
Nov 27, 2008 | Empire GWT-25 Wall Mounted Panel Heater
May 15, 2008 | Dayton Heating & Cooling
Dec 28, 2008 | Empire GWT-25 Wall Mounted Panel Heater
139 people viewed this question
Usually answered in minutes!