Question about Heating & Cooling
Goodman furnace PGB024075-1
First step turn the thermostat off. It is very important.
Next find the knob on top of the gas valve you will see writing on it turn it to pilot it could be in the off position so move it to pilot depress the knob where it goes down about one inch. Take a long lighter long match or something like that and hold at the pilot it will be back in the furnace by the front of the burners. Once the pilot lights hold the button for another 30 seconds. Release the knob now the pilot should be on and the next step is why you turned off the thermostat rotate the knob to on position. Go to the t-stat and turn on the heat.
Posted on Nov 27, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jan 19, 2016 | Goodman Manufacturing Goodman GMS81005CN...
Feb 27, 2014 | Goodman Manufacturing Goodman...
May 01, 2011 | Heating & Cooling
Mar 28, 2011 | Heating & Cooling
Dec 12, 2010 | Heating & Cooling
Jan 01, 2009 | Heating & Cooling
Dec 17, 2008 | Heating & Cooling
Dec 16, 2008 | Heating & Cooling
Nov 03, 2007 | Carrier XHB123D X/Y Series Heat/Cool Air...
227 people viewed this question
Usually answered in minutes!