Question about Amana ABC2037SS Air Conditioner
Ok sounds like your transformer is not working. Now as long as no one has removed the doors to the furnace cabinet and they are in place just like the are suppose to be, because there is a door switch that turns off the power to the whole unit until the door is in place correctly. Find the circuit board and look to see it you have a fuse on the board it will look like a car fuse the spade type they are 5 amp fuses. If it is good find the transformer and replace it. If you feel comfortable around electricity there are two sides to the transformer line voltage which is 120 and the secondary side which is 24 volts. If you have a volt ohm meter ohm out the transformer each side line side and low voltage side. An open on either side will be noticed and then replace the transformer. I know this is alot of things to check but just elimanating everything it could be before condemming the transformer. Turn the main breaker off and replace.
Posted on Nov 27, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Feb 02, 2013 | Amana In Wall Install Kit For Digismart...
Nov 05, 2012 | Siemens RWB29
Jul 31, 2011 | Amana Heating & Cooling
Apr 08, 2010 | Ruud UAMB042 Air Conditioner
Nov 07, 2009 | Ruud Central System Air Conditioner
Nov 04, 2009 | Vulcan AUW230A Heater
Mar 16, 2009 | Amana PTC153B50AM Split System Air...
Jan 23, 2009 | GE Zoneline AZ38H12DAD Split System Air...
686 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: