Question about Heating & Cooling
The fault occured a few days after I altered the radiator layout and then refilled the system. Intially the boiler worked fine, then a few days later all of the temperature lights light upto 80 and the boiler would not fire. The pump was working but the fan was not. After diagnosing the electronics I came to the conclusion it was either the contol pcb or the temperature probe. As the temperature probe was the cheaper option I replaced that first. The system is now working again. I think this fault was caused by me failing to completly remove all air from the system after refill and an air lock occuring causing the probe to burn out.
Posted on May 07, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Oct 17, 2015 | Amana Heating & Cooling
Nov 16, 2014 | Heating & Cooling
Aug 28, 2010 | Heating & Cooling
Aug 27, 2010 | Heating & Cooling
Jan 19, 2009 | Heating & Cooling
Dec 31, 2008 | Heating & Cooling
Dec 03, 2008 | Heating & Cooling
Nov 28, 2008 | Heating & Cooling
Nov 19, 2008 | Heating & Cooling
Oct 26, 2008 | Heating & Cooling
414 people viewed this question
Usually answered in minutes!