Question about Arctic Air 22 cu. ft. Commercial Freezer F22CWF
We have operated a Artic Air model F22CWF2 freezer at our church for one year. I understand that a vertical flexible hose on the rear of the unit is part of the automatic defrost sysyem. The tube becomes plugged with froozen ice which stops the air flow and permits ice to accumulate inside the box. What can be done?
Remove the back cover to access the top of that drain line. Take some table salt in a tablespoon and dump in the tube. Will drain so fast you won't believe it. Might have a big build up of ice blocking the top so get your hair dryer and defrost that big build up. Flush with small amount of water and monitor the drain pan located under neath the freezer. hope this was helpfull
Posted on Nov 26, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jul 29, 2015 | Artic Air Arctic Air 65055K Shelf Kit for...
Oct 16, 2014 | Artic Air Used F22CWF4 White Commercial...
Nov 06, 2017 | Artic Air Arctic Air AF49 Commercial...
Aug 22, 2010 | Freezers
Sep 04, 2009 | Maytag Freezers
Aug 17, 2009 | Freezers
Aug 16, 2009 | Kenmore 13.7 cu. ft. / 388 liter Upright...
Aug 13, 2009 | Freezers
294 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: