Question about Dayton Heating & Cooling
THIS HEATER (3E369D) IS POSSESSED. OVER THE PAST SEVERAL YEARS IT HAS CONSUMED MANY TRANSFORMERS. SOMETIMES IT WOULD USE 2 PER SEASON(2MONTHS), SOMETIMES IT WOULD LAST 2 DAYS. ONE ACTUALLY LASTED 2 YEARS. NEED SOME INFO ON WHAT THE MOST LIKELY COMPONENT WOULD BE AT FAULT OR IF THIS IS A COMMON PROBLEM AND WHAT IS THE FIX?
You obviously have an intermittent low voltage short. I would visually inspect all low voltage wiring to try to locate the problem. Pay good attention to the limit circuit, I have seen wires melted to the inducer housing before causing this problem. also, install a 3A fuse inline till you find the problem to save on transformers.
Posted on Nov 26, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jan 26, 2013 | American Standard Trane Ge Gas Furnace...
Oct 30, 2012 | Intermatic Malibu 121W Power Pack...
Jul 06, 2011 | Jandy AQUALINK RS TELELINK KIT
May 22, 2011 | Teledyne Laars Laars Lite 2 Pool Heater...
Oct 17, 2010 | Hayward H-series Electronic Gas Pool...
Jun 24, 2010 | Hayward 250kbtu Ng Pool Heater - Inground
Jan 19, 2010 | Altec Lansing ATP 3W Computer Speakers
Jan 04, 2009 | Audio Players & Recorders
Nov 25, 2008 | Heating & Cooling
Jan 04, 2008 | Goodman GMS90703BXA Heater
85 people viewed this question
Usually answered in minutes!