Question about Heating & Cooling
You likely have a bad thermocouple. Go to a hardware store and pick one up. You will need to shut off your furnace and remove the little copper wire that goes into your gas valve where you are holding down the button to light the pilot. Don't remove the larger silver tube that is for your pilot valve to supply the gas to the pilot. Follow the copper line and try to pull straight down out of the pilot assembly and it may slide right out. If it doesn't you will need to remove the pilot assembly so go ahead and remove the larger silver tube from the gas valve as well. Take out the one or two screws mounting the pilot assembly usually a 1/4 inch or 5/16 nutdriver should be the proper tool. Once removed unscrew the thermocouple and put in the new one. Reassemble. Careful not to bend your silver pilot tubing too much otherwise you will need to replace that as well. Always check for gas leaks around your pilot tube after reinstalling parts.
Posted on Nov 24, 2008
a 6ya Repairman can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repair professionals here in the US.
click here to Talk to a Repairman (only for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Mar 02, 2015 | Heating & Cooling
Jan 11, 2013 | Bosch Worcester Spark Electrode...
Oct 27, 2012 | Heating & Cooling
Aug 23, 2011 | Water Heaters
Feb 20, 2011 | Heating & Cooling
Jul 27, 2017 | Heating & Cooling
Dec 22, 2009 | Williams 3003622 Ceramic Wall Mounted...
Nov 27, 2009 | Kenmore Elite 900 sq. in. Cooking Area Gas...
Sep 25, 2008 | Whirlpool Heating & Cooling
82 people viewed this question
Usually answered in minutes!