Question about Heating & Cooling
You likely have a bad thermocouple. Go to a hardware store and pick one up. You will need to shut off your furnace and remove the little copper wire that goes into your gas valve where you are holding down the button to light the pilot. Don't remove the larger silver tube that is for your pilot valve to supply the gas to the pilot. Follow the copper line and try to pull straight down out of the pilot assembly and it may slide right out. If it doesn't you will need to remove the pilot assembly so go ahead and remove the larger silver tube from the gas valve as well. Take out the one or two screws mounting the pilot assembly usually a 1/4 inch or 5/16 nutdriver should be the proper tool. Once removed unscrew the thermocouple and put in the new one. Reassemble. Careful not to bend your silver pilot tubing too much otherwise you will need to replace that as well. Always check for gas leaks around your pilot tube after reinstalling parts.
Posted on Nov 24, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jan 11, 2013 | Bosch Worcester Spark Electrode...
Apr 20, 2012 | Heating & Cooling
Apr 24, 2011 | Heating & Cooling
Feb 03, 2011 | Procom ML300HGA Heater
Jan 05, 2010 | 2002 Mitsubishi Galant
Dec 22, 2009 | Williams 3003622 Ceramic Wall Mounted...
Nov 27, 2009 | Kenmore Elite 900 sq. in. Cooking Area Gas...
May 28, 2009 | Bosch AquaStar 125FXKIT-NG 125FX Natural...
Nov 24, 2008 | Heating & Cooling
59 people viewed this question
Usually answered in minutes!