Question about Heating & Cooling
I can turn the power off at the furnace and then restart it and it will run a cycle again.... but if i don't go up and turn the power off from the furnace it will not turn the burners back on for another heat cycle.. i have been told it is the limit switch and i would like to know how it should test if it is good with a volt ohm meter.. when it is cool it still reads closed... does that mean it needs replaced?
...........betty (: dallas
Probably need to replace the limit. Pull the wires off of the limit and set your meter to ohms. If it beeps while holding one test lead on each of the connectors on the limit itself then it should be good. If no beep it may be stuck, still too hot, or bad part. Try to give it a whack with something solid like the end of a screwdriver sometimes this will release a stuck limit. If you get it to fire up and heat again make sure your blower comes on and your filter is cleaned. You need to check the temperature rise on your furnace afterwards. Limits dont trip for no reason usually.
Posted on Nov 24, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Nov 20, 2014 | Intertherm Heating & Cooling
Jan 09, 2013 | Gibson Nordyne GR6GD-X42K072C 3.5 Ton 13...
Sep 24, 2011 | Ruud UBHC Air Conditioner
Jul 03, 2011 | Heating & Cooling
Mar 09, 2009 | Carrier Heating & Cooling
Mar 08, 2009 | Carrier XHB123D X/Y Series Heat/Cool Air...
Feb 06, 2009 | Carrier Heating & Cooling
Nov 24, 2008 | Heating & Cooling
May 13, 2008 | Heating & Cooling
Dec 13, 2007 | Carrier XHD183D Air Conditioner
170 people viewed this question
Usually answered in minutes!