Question about General Filters 1042-LH Humidifier
I checked to see if water was getting to inlet of motor and it did. Does not seem to get past little motor that puts water up to top of Humidifier.
That is not a 'motor' on the side of the humidifier housing, it is a solenoid valve. The water feeds in to one side and exits the other side to a tube that feeds in to the top of the humidifier unit. The valve opens and allows water to flow when electrical power is applied to the valve
The valve electircal requirement may be either 120 vac or 24 vac. Power typically is switched on and off by a Humidistat control. The power feed to the Humidistat may come from a small transformer if the valve is a 24 vac unit, or directly from a furnace connection if the valve is a 120 vac unit. There are many variations, though.
A qualified licensed eletrician should check the power feed to the valve. If there is no power feed to the valve then he can trace back to the point of failure and correct the issue ... but he must also check for additional issues with the valve itself, as noted below.
Other possibles reasons for solenoid valve failure:
If power feed to the valve tests ok, then the coil inside the solenoid may be 'open' (bad, no continuity). The electrician can test the coil by checking resistance or continuity of the coil.
A non-electrical problem is that the valve path may be blocked by hardwater mineral build-up or other foreign material that flowed through the water line.
The solenoid valve must be replaced if either of the above is true with your valve.
Remember, use only a quailified licensed electrician!
Posted on Jan 23, 2009
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Tips for a great answer:
Jan 07, 2018 | Germ Guardian H2000 14 Gallon Humidifier
Jan 31, 2011 | Aprilaire 700 Humidifier
Dec 30, 2010 | General Filters 1042-LH Humidifier
Dec 14, 2009 | Honeywell HE360A1027 Whole House...
Dec 13, 2009 | Honeywell HE220A1019 Whole House...
Nov 07, 2009 | Aprilaire 700 Humidifier
Feb 05, 2009 | Honeywell HE220A1019 Whole House...
Dec 25, 2008 | Aprilaire 700 Humidifier
Dec 28, 2007 | Honeywell HE220A1019 Whole House...
Jan 18, 2006 | Honeywell HCM530 Humidifier
783 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: