Question about Goodman GMS90703BXA Heater
I replaced gas valve ,I have 24 volts to gas valve,I have 3 volts from flame sensor. is it the igniton module or sensor? HELP!!
Your flame sensor is measured in Millivolts not voltage. Is the flame spreading accross the burners at all? If it only ignites on one of the burners, you have debris blocking the flame spreader. Clean the burners and flame spreader bar. If you just as you say get a pilot, clean the flame rod.
Posted on Nov 25, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Dec 29, 2014 | Heating & Cooling
Feb 23, 2014 | Honeywell Intermittent Pilot Module...
Nov 18, 2013 | Honeywell Furnace Gas Valve Sv9501h2409
May 16, 2010 | Goodman GDS80703ANA Open Flame Mid-Size...
Mar 05, 2010 | Goodman GMS90703BXA Heater
Jan 26, 2010 | Goodman GMS80453ANA Open Flame Mid-Size...
Nov 18, 2009 | Goodman GDS80904BNA Open Flame Heater
Oct 18, 2009 | Goodman Heating & Cooling
Jan 07, 2009 | Goodman GMS90703BXA Heater
115 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: