Question about Pool & Spa
I have a Pentair MiniMax NT 250,000 btu pool heater that failsto ignite burners. the ignition element heats up and glows. the deviceattempts to light the burners three (3) times and then displays anerror...error code 04. the PLC on the inside had a red indicator lightthat blinks three(3) time which according to the key on the PLCindicates a fuel valve lock out. i have reset the heater by switchingit off and also by unplugging the unite for 10 minutes and no luck. anythoughts or suggestions?? please advise. thanks. rsm
1. There is air in the gas line. Power down the heater and allow it to try igniting until lockout. If it locks out, repeat the process. Most lines will clear within 4-5 attempts to ignite.
2. A plugged burner orifice. Run a small pipe cleaner in the brass fittings on the burner tray. They may have small webs in them restricting gas flow.
If the unit is a Standard (STD on the plate inside) it has a flame sensor that may also be bad. That sensor is on the end of the single wire that is cloase to the ignitor wire near the burners. Also check for a losse ground wire on the heater.
Posted on Dec 21, 2008
Could be inducer fan motor. On acall for heat inducer fan motor start the ignites the burner. The unit has to realize air flow. If inducer fan motor ok, check pilot assembly valve there is and adjustment screw on the valve body
Posted on Feb 06, 2009
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Tips for a great answer:
Jun 08, 2012 | Pentair Minimax NT Heater
Jul 26, 2010 | Pentair Minimax Ch 250,000 Btu Natural Gas...
Jun 30, 2017 | Pentair Minimax Ch 400,000 Btu Propane...
Sep 29, 2017 | Pentair Minimax NT Heater
Oct 08, 2009 | Pentair Minimax Ch 250,000 Btu Natural Gas...
Jul 15, 2009 | Pentair MINIMAX NT TSI IGNITER
Sep 26, 2017 | Pentair Minimax Ch 250,000 Btu Natural Gas...
1,235 people viewed this question
Usually answered in minutes!