Question about Heating & Cooling
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
OK lets see what we can help you with here. The condensate drain is clogged. There are a couple of ways to clear this clog so lets give it a try. If you know where the drain for the a/c is located outside (usually by the outside condenser unit) it will be a pipe that is just sticking out of the side of the house, if you find it take a wet/dry vac and place it on this pipe and turn the vacuum on and make a seal with your hand this should unclog the drain. If you don't find this pipe outside the house then go to the furnace and you will see at the bottom of the furnace a pipe (PVC) white, this is the drain for the unit inside. Take the wet/dry vac and have it at the ready in the event the clog is further down the line than at the furnace itself now the fittings on this pipe should not be glued together due to the ability to access for this very purpose. Take the pipe apart at one of the fittings and place the wet/dry vac on the end of the pipe towards the furnace and using your hand make a seal and evacuate the line. Do this to both sides since you don't know where the blockage is. If you are unable to separate the pipe at any fitting you will need to cut the pipe and at the spot of the cut you will need to repair it with a sleeve. Remember that the drain pipe is plastic and is made of pvc so you can get a repair coupling from any home improvement store for this repair.
Hope this helped you some
Posted on Feb 21, 2010
Here is where you can find all the info you will ever need about Mitsubishi Air Conditioning units...
Check out this tip that I wrote about that...
Mitsubishi Air Conditioner Troubleshooting and Repair
Posted on Aug 20, 2010
Today I install a new unit Panasonic CS-S13KKP also have a same problem timer blink and the outdoor unit wont start. Error code is 11. after checking the problem, can not using a 3 cable cord, solve the problem using 4 Cable cord and its run !
Posted on Dec 11, 2010
Tips for a great answer:
Oct 31, 2013 | Panasonic Heating & Cooling
Sep 08, 2011 | Panasonic Heating & Cooling
Jul 13, 2011 | Panasonic CW-XC243HU Air Conditioner
Dec 30, 2010 | Panasonic CS-A12C Air Conditioner
Sep 02, 2010 | Panasonic Room Air Conditioner CWXC104HU
Nov 21, 2009 | Toyotomi TID-1800HP Air Conditioner
Aug 21, 2009 | Panasonic Heating & Cooling
Aug 20, 2009 | Panasonic CW-XC203EU Air Conditioner
Jun 10, 2009 | Panasonic MCM INVERTER
Aug 15, 2018 | Heating & Cooling
60 people viewed this question
Usually answered in minutes!