Question about Heating & Cooling
WHEN YOU TURN ON THE HEATER, IT WILL CYCLE ON. WHEN THE BURNER STSTUS REACHES HALF WAY IT SHUTS DOWN WITH THE BURNER STATUS LIGHT FLASHING. PLEASE HELP!
Not sure exactly what is meant by half way it shuts off. My furnance wouldn't heat to 68 degrees from a setting of 63 degrees on the setback thermostat without shutting down several times with a single flashing led. It would reset after an hour or so until it finally reached the 68 degrees. The problem turned out to be the tube that drains the water from the blower assembly. It had a belly in the middle which would cause the water to sit and block the airflow sensor for the gas value. Lifted tube to allow proper drainage to correct.
Posted on Dec 24, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Nov 17, 2014 | Heating & Cooling
Oct 06, 2014 | Coleman Propane Forced Air Heater...
Mar 09, 2013 | Heating & Cooling
Jan 04, 2013 | Heating & Cooling
Nov 21, 2009 | Dayton Electric Heater
Oct 16, 2009 | Slant Fin Heating & Cooling
Mar 16, 2009 | Mr. Heater Natural Gas Garage Heater -...
Dec 09, 2008 | Rinnai Toyostove Direct Vent Heater:...
Dec 28, 2007 | Goodman GMS80904BNA Open Flame Mid-Size...
389 people viewed this question
Usually answered in minutes!