Question about Heating & Cooling
WHEN YOU TURN ON THE HEATER, IT WILL CYCLE ON. WHEN THE BURNER STSTUS REACHES HALF WAY IT SHUTS DOWN WITH THE BURNER STATUS LIGHT FLASHING. PLEASE HELP!
Not sure exactly what is meant by half way it shuts off. My furnance wouldn't heat to 68 degrees from a setting of 63 degrees on the setback thermostat without shutting down several times with a single flashing led. It would reset after an hour or so until it finally reached the 68 degrees. The problem turned out to be the tube that drains the water from the blower assembly. It had a belly in the middle which would cause the water to sit and block the airflow sensor for the gas value. Lifted tube to allow proper drainage to correct.
Posted on Dec 24, 2008
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Tips for a great answer:
Oct 06, 2014 | Coleman Propane Forced Air Heater...
Jan 04, 2013 | Heating & Cooling
Jan 17, 2011 | Heating & Cooling
Sep 10, 2010 | Saeco Odea Go
Jun 22, 2010 | Dryers
Oct 16, 2009 | Slant Fin Heating & Cooling
Mar 16, 2009 | Mr. Heater Natural Gas Garage Heater -...
Dec 09, 2008 | Rinnai Toyostove Direct Vent Heater:...
425 people viewed this question
Usually answered in minutes!