Question about Heating & Cooling
I have a heat strip in a package unit. It has two 60a breakers on the strip. Do I need two seperate 60 amp circuits or can they be loop togeother
DO YOU MEAN FEED IN OR FEEDING HEATING ELEMENT . I ASSUME YOU MEAN TO FEED FROM PANEL THE ANSWER IS YOU MUST RUN 2 CIRCUITS OF 3-cond #6 copper to unit connect the feeds to one breaker and the other circuit to the other breaker the neutrals connect to lug provided or purchase them and frame gnd to case , i would not recommend anything except copper as most mfg do not rec aluminum because on the heating and cooling of the unit and conductors
Posted on Nov 24, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Aug 17, 2012 | Goodman Heating & Cooling
Aug 26, 2011 | Heating & Cooling
Apr 21, 2011 | Heating & Cooling
Apr 01, 2011 | Heating & Cooling
Jan 11, 2010 | Heating & Cooling
Dec 07, 2009 | Goodman CKL42AR42 Air Conditioner
Jul 14, 2009 | Heating & Cooling
Oct 22, 2008 | Hampton Bay HBLG5004 Air Conditioner
Jan 19, 2017 | Heating & Cooling
117 people viewed this question
Usually answered in minutes!