Question about Freezers
Traulsen refridgerator freezer model ur 48 dt freezer doesent get below 10 deg
The first place to look is to check the charge. Using guages check the low and high side pressures and their relationship to one another. I'm assuming your unit is a R-404 unit which, if fully charged and the condenser is clean, and the fan is operating, should have about 210 to 250 high side pressure. Other things to check: evaporator coil ice/frost free; defrosting properly to obtain a clean coil; all evaporator fans running. If low side pressure is above 30 PSI you have a weak compressor. Whatever, fix the Traulsen unit, its head and shoulders above anything else on the market today.
Posted on Nov 24, 2008
Tips for a great answer:
Sep 28, 2015 | Traulsen Freezers
Jan 13, 2011 | Traulsen Reach in Freezer - G22010
May 20, 2010 | Traulsen 46 cu. ft. / 1303 liter...
Jan 07, 2010 | Traulsen 46 cu. ft. Upright Freezer G22011
Oct 02, 2009 | Traulsen 46 cu. ft. / 1303 liter...
Aug 19, 2009 | Traulsen 7 cu. ft. / 198 liter Commercial...
Jul 17, 2009 | Freezers
Dec 10, 2016 | Freezers
Dec 07, 2016 | Freezers
325 people viewed this question
Usually answered in minutes!