Question about Heating & Cooling
Which turbomax, as there a two different models. The more modern one, with the brass CPL diverter valve, located at the front left of the boiler, was very prone sticking & jamming, this would restrict flow through the hot water circuit in the boiler, and cause cycling. Vaillant actually modified the diverter. You can identify, if it is the old type, as there is a very small hole in the middle of the diverter on the old ones, probable no more than 1mm-2mm wide. The modfied one, is much bigger approx 5mm wide. If old type, replace as this usally sorts the problem
Posted on Mar 03, 2009
I had this. Open up the main case, take the second inner case front off to expose the boiler.
Clean the thermocouple which detects the flame being lit with some steel wool held with needle nose pliers. It will be all sooty and will turn off the gas as a safety precaution if it does not detect heat fast enough.
Don't listen to the gas man who will say "needs a new circuit board mate" as this is usually a stock response.
Posted on Jan 05, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Oct 03, 2013 | Heating & Cooling
Aug 31, 2009 | Water Heaters
Jul 16, 2009 | Water Heaters
Apr 13, 2009 | Air Purifiers
Dec 31, 2008 | Heating & Cooling
Dec 15, 2008 | Water Heaters
Oct 05, 2008 | Heating & Cooling
699 people viewed this question
Usually answered in minutes!