Question about Honeywell Heating & Cooling
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Typically if you have a yellow wire in the "y" terminal blue is used as common or "c". As far as your jumper from rc to rh, that will depend upon what type of heat you have. If all of your heat and cooling come from your packaged unit outside, yes you will need the jumper. If this does not work maybe you have a bad breaker or transfomer.
Posted on Oct 14, 2007
Hopefully there are markings on the old t-stat as to what terminal is what.
on the honeywell 8000 use the heat pump labeling and then the standard wiring would be
There should not be a bare wire, it probably just has the insulation stripped back way too far.
You should probably open the furnace and compare the terminal label in the furnace to the wire color. normally yellow and blue pass through the furnace and are wire nutted to wires going to the outdoor unit. In the furnace the white wire will connect to the w or w1 terminal. also, you will need to set the Honeywell stat to have the following parameters.
other parameters that I did not specify, you may read the manual and make your own decision but I recommend factory settings for the other parameters
Posted on Jun 18, 2008
The red/blue cover just hides the screw that allows you to remove the handle.
Turn off the water :-)
Remove the handle, you will see that part of the faucet is a large half moon nut. sometimes you can loosen these with your hands, but most times you will need a tool. To avoid damaging the finish with the tool, use smooth jaw tools or protect the nut with a thin piece of rubber/cardboard etc between the jaws of the tool and the nut.
You can then remove the ball/stem, the washers and springs.
Replace the stem, washers and springs and reassemble just as you took it apart.
Be carefull that the little "nipple" lines up with the notches properly.
Take care that you know exactly how it came apart and which direction each prt was facing.
Posted on Dec 06, 2008
Tips for a great answer:
Nov 08, 2017 | Honeywell Heating & Cooling
Sep 13, 2008 | Honeywell Heating & Cooling
Jun 22, 2015 | Heating & Cooling
Oct 05, 2017 | Honeywell L8124G1020 Triple Aquastat Relay...
Nov 22, 2012 | General Electric GE SmartWater Household...
Jun 06, 2011 | Honeywell L4103A1019 combination aquastat....
May 09, 2017 | Honeywell Heating & Cooling
Nov 03, 2009 | Honeywell Electronic Programmable...
Jul 23, 2008 | Honeywell Heating & Cooling
84 people viewed this question
Usually answered in minutes!