Question about Heating & Cooling
I have a light that is flashing three times which indicates that the pressure switch is open and should be closed. how do i close it?
Sounds like the flue is plugged, I had same problem and opened up the draft fan and there was a dead bird restricting the flue. Furnace will never light if the pressure switch never closes as you have found out. Also has anyone moved the switch some are position sensitive meaning have to be in same position factory set the switch. I had one like that also switch was little crooked so I straighten it up and walla worked.
Posted on Nov 23, 2008
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Nov 08, 2016 | Heating & Cooling
Jan 19, 2015 | Armstrong Lennox Ducane Armstrong Gas...
Feb 14, 2014 | Coleman 7990-319p Evcon Gas Furnace...
Nov 12, 2013 | Heating & Cooling
Nov 05, 2013 | Honeywell Furnace Air Pressure Switch...
Oct 06, 2012 | Honeywell Furnace Air Pressure Switch...
Nov 12, 2011 | Heating & Cooling
Jan 10, 2010 | Armstrong H 67 1PH Bf In Line Circulator...
Sep 12, 2008 | Heating & Cooling
Mar 23, 2008 | Heating & Cooling
May 23, 2018 | Heating & Cooling
916 people viewed this question
Usually answered in minutes!