Question about Weather King Heating & Cooling
I cleaned every thing you can see and I still can not get it to work.
If we do not turn on the heater for a few hour it will start on its own
but once it stops it will continue to go for 10 second stop and it
will just continue to on off, on off every 10 seconds.
If you are talking about a furnace the problem sounds like the flame proving device located at the end of the burners. Looks like a solid wire hanging down into the flame. Take some steel wool and gently remove the carbon that has built up on the surface. Don't get rough with it as just a mild touch will be good.
Posted on Nov 23, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Aug 31, 2012 | Frigidaire FTF2140FS Front Load Washer 10...
Jan 09, 2011 | Weather King 10AJA3001AH Air Conditioner
Dec 22, 2010 | Weather King Heating & Cooling
Dec 10, 2010 | Heating & Cooling
Jul 08, 2010 | Weather King 10AJA4201AH Air Conditioner
May 14, 2009 | Weather King 12AJA4801AH Air Conditioner
Jun 10, 2008 | Weather King 10AJA3601AH Air Conditioner
Dec 21, 2007 | Weather King 12AJA4801AH Air Conditioner
70 people viewed this question
Usually answered in minutes!