Question about York Yankees Bedding MLB Comforter
SOURCE: Heat pump wiring
yes i can , you need to hookup the r and the o together so that the reversing vvalvce is allways energized . so with that im mind send r,y,c,o to theout side unit. at the ahu you'll hook up the 5 wires for the furnace, r g w1 w2 com and at the thermostat r,w1,w2,y,g,com,o then you will be set (the o get hooked up to o and goes straight out side.
Posted on Dec 25, 2008
has anyone worked on this furnace because the error would indicate that the positive 120 volt and the neg 120 volt is swapped , these units will also do this when the ground wire to the furnace or gas valve or furnace or @ the panel is lose , corroded , or missing , the gnd must be present to open valve , I am aware that ac is is not usually polarity sensitive but in this case it most certainly is ...have seen many time and know it to be true
Posted on Jan 01, 2009
You should call a professional in on this one you can damage alot of expensive parts trying to do this on your own without the proper tools and knowledge of the control logic
Posted on Sep 17, 2009
Testimonial: "OK...that's what I thought but figured I would attempt it myself, if possible. I will call my local heat/ac guys to install the cutoff switch. Thanks!"
This flame is not likely going off on a high limit due to clogged filters as suggested previously because the unit goes off on safety before the blower comes on. If it works sometimes and not others it is most likely a flame sense issue or an electronic problem. If the boards logic tells the inducer to keep running if it thinks the flame is lost this may be your clue. You can attempt to find the red LED trouble light on the circuit board(or in burner compartment) and this may tell you exactly what the problem is but you may need to tape the door interlock switch so you don't loose the code when you open the blower compartment. You can clean flame sensor with very fine sandpaper or steel wool but replacement is usually the best.
Posted on Jan 11, 2010
Tips for a great answer:
Jan 11, 2011 | York Yankees Bedding MLB Comforter
Nov 26, 2009 | York Yankees Bedding MLB Comforter
Nov 18, 2009 | York Yankees Bedding MLB Comforter
Sep 05, 2009 | York Yankees Bedding MLB Comforter
Jan 16, 2009 | York Yankees Bedding MLB Comforter
Jan 10, 2009 | York Yankees Bedding MLB Comforter
Dec 27, 2008 | York Yankees Bedding MLB Comforter
Dec 21, 2008 | York Yankees Bedding MLB Comforter
Dec 03, 2008 | York Yankees Bedding MLB Comforter
394 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: