Question about York Yankees Bedding MLB Comforter
SOURCE: Heat pump wiring
yes i can , you need to hookup the r and the o together so that the reversing vvalvce is allways energized . so with that im mind send r,y,c,o to theout side unit. at the ahu you'll hook up the 5 wires for the furnace, r g w1 w2 com and at the thermostat r,w1,w2,y,g,com,o then you will be set (the o get hooked up to o and goes straight out side.
Posted on Dec 25, 2008
has anyone worked on this furnace because the error would indicate that the positive 120 volt and the neg 120 volt is swapped , these units will also do this when the ground wire to the furnace or gas valve or furnace or @ the panel is lose , corroded , or missing , the gnd must be present to open valve , I am aware that ac is is not usually polarity sensitive but in this case it most certainly is ...have seen many time and know it to be true
Posted on Jan 01, 2009
You should call a professional in on this one you can damage alot of expensive parts trying to do this on your own without the proper tools and knowledge of the control logic
Posted on Sep 17, 2009
Testimonial: "OK...that's what I thought but figured I would attempt it myself, if possible. I will call my local heat/ac guys to install the cutoff switch. Thanks!"
Tips for a great answer:
Jan 11, 2011 | York Yankees Bedding MLB Comforter
Nov 26, 2009 | York Yankees Bedding MLB Comforter
Nov 18, 2009 | York Yankees Bedding MLB Comforter
Sep 05, 2009 | York Yankees Bedding MLB Comforter
Jan 16, 2009 | York Yankees Bedding MLB Comforter
Jan 10, 2009 | York Yankees Bedding MLB Comforter
Dec 27, 2008 | York Yankees Bedding MLB Comforter
Dec 21, 2008 | York Yankees Bedding MLB Comforter
Dec 03, 2008 | York Yankees Bedding MLB Comforter
397 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: