Question about Honeywell HE365 Humidifier
I have a Honeywell Powered Flow Thru Humidifier (HE365)
It;s always worked fine except this year I am not getthing any water flow to thr unit. The water supply valve is open but no water reaches the unit. Any suggestion?
Loosen the brass fitting where it connects to the soleniod valve. If water comes out your saddle valve is ok. Carefully retighten this fitting. With the humidifier turned on loosen the first fitting down stream from the valve see if water comes out. if it does turn the humidifier off and see if it stops, it should. That will tell you the the valve is ok then, just clean the filter and the oriface. if it does not turn on and off check the wiring. if ok replace the valve.
Posted on Mar 29, 2009
Tips for a great answer:
Feb 03, 2011 | Honeywell HE365 Humidifier
Jan 24, 2011 | Honeywell HE365 Humidifier
Dec 07, 2010 | Honeywell HE365 Humidifier
Nov 26, 2010 | Honeywell HE365 Humidifier
Dec 30, 2009 | Honeywell HE220A1019 Whole House...
Oct 15, 2009 | Honeywell HE365 Humidifier
Apr 17, 2009 | Honeywell HE365 Humidifier
681 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: