Question about Heating & Cooling
a 6ya Repairman can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repair professionals here in the US.
click here to Talk to a Repairman (only for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
SOURCE: My oil boiler is a
The actual final solution was to replace the fuel valve/solenoid following which the boiler has run without failure.
The conclusion was that the fuel valve solenoid was ok when cold but when heated up had some sort of electrical breakdown in its coils, causing the fuel valve to fluctuate until the boiler locked out.
Posted on Oct 17, 2008
SOURCE: How to replace collapsed fire
Your heating supply store will have a replacement unit. I do suggest you get a pro to do this, however. Your burner should be tuned and this is not a job for an amateur.
Posted on Nov 15, 2008
Tips for a great answer:
Oct 23, 2016 | Heating & Cooling
Feb 08, 2014 | Weil-McLain CGa-25-SPDN, NG, Gas Fired...
Dec 07, 2017 | Heating & Cooling
Feb 18, 2013 | Weil-McLain CGa-25-SPDN, NG, Gas Fired...
Nov 06, 2012 | Heating & Cooling
Apr 20, 2010 | Heating & Cooling
Oct 22, 2008 | Honeywell Heating & Cooling
Feb 18, 2018 | Heating & Cooling
71 people viewed this question
Usually answered in minutes!