Question about Weather King 10AJA3601AH Air Conditioner
Then the igniter lights then the gas valve opens . now this is where it really becomes technical the flame ignites for approx 15 sec and goes out. thought flame sensor or circuit board replaced both of them and it still does the same thing. also checked the wiring connections through all the plugs. I am an experienced hvac tech but am lost here anyone have any advice
My furnace did the same and I found a small crack in the hose going from the exaust fan to a presure switch. I cut the bad piece out and started working fine.
Posted on Dec 15, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Oct 24, 2015 | Goodman Heating & Cooling
Oct 07, 2014 | Coleman 7990-319p Evcon Gas Furnace...
Jan 10, 2014 | Heating & Cooling
Nov 01, 2013 | Heating & Cooling
May 06, 2011 | Bionaire Heating & Cooling
May 04, 2010 | Goodman GMS90703BXA Heater
Jan 16, 2010 | Weather King Heating & Cooling
Jan 01, 2010 | Carrier XHB123D X/Y Series Heat/Cool Air...
Nov 23, 2009 | Heating & Cooling
Oct 27, 2008 | Goodman GDS80904BNA Open Flame Heater
358 people viewed this question
Usually answered in minutes!