Question about Weather King 10AJA4201AH Air Conditioner
Hello. The fan will run if the thermostat is set at cool and on. Or cool and auto. The fan will run if put to heat and on but NOT heat and auto. Then we removed the top halfs panel and there was a yellow wire that was hanging lose with no cap on it. There was one wire with a cap made for two wires but only one inside. my husband put the yellow wire in with the red or purple I think and saw smoke shoot out of a little black box on the left side of the panel if looking at it. This box had wires going to it. Now nothing works. It is a 24* night here in Phenix City Al. and we have 4 children. PLEASE PLEASE PLEASE HELP As soon as Possible. Thanks Brandi
He shorted the Transformer and lost all the 24v low voltage controls. This could have possibly been a loose wire in the T-stat or even a defective T-stat. It could have even been a reversing valve in some cases. Unit would only run auxillary heat bank in on position.
Posted on Aug 29, 2010
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Nov 01, 2015 | Heating & Cooling
Dec 30, 2010 | Weather King 10PJA4301AH Air Conditioner
Nov 16, 2010 | Weather King 10AJA6001AH Air Conditioner
Oct 30, 2009 | Weather King 10AJA6001AH Air Conditioner
Jul 26, 2009 | Heating & Cooling
Dec 16, 2008 | Weather King 12AJA6001AH Air Conditioner
Sep 18, 2008 | Heating & Cooling
May 21, 2008 | Weather King 10AJA2501AH Air Conditioner
May 06, 2008 | Weather King 10AJA2501AH Air Conditioner
66 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: