Question about SySTOR Systems (400S52) Burner
We filled the tank, had the furnace turned off for a few hours and when we relite the furnace it wouldn't light, changed the nozzle and it works but rumbles. what is the setting for a miller gun furnace electrode?
and what nozzle do you recomend?
Varies from burner to burner to burner , should replace with the same as you removed , the numbers are very important on the nozzle one of the numbers is the degree of the fire pattern the nozzle produces ex. a 90 degree or 80 degree etc . this is determined by the way the fire box in the furnace is insulated . the other number is gallons per hour of oil the furnace is set up to use , ex. .70 gph or .80 gph all of these numbers are critical and should not be changed except by an expert or you could damage your furnace and could possibly be dangerous . the numbers will be on your old nozzle and should go back with same one , as to the adjustment , they also vary ,but i can give you one that will usually work for most furnaces , that is one eighth inch space between electrode tips , five eights in front of nozzle port opening , and one half inch above center of nozzle center , where the hole is . bleed all air out of system after installing nozzle , let me know if no fix have more ideas
Posted on Jan 01, 2009
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Nov 26, 2014 | Rheem Gas Furnace 75000 Btu 80% Afue. Rgpn...
May 22, 2011 | Barbeques Galore 38-inch Grand Turbo...
Mar 03, 2011 | Empire Direct Vent Wall Furnace;...
Nov 03, 2017 | 2002 Nissan Altima
Jan 22, 2011 | Heating & Cooling
Nov 24, 2010 | Honeywell Heating & Cooling
Nov 23, 2010 | Heating & Cooling
Apr 26, 2010 | Heating & Cooling
Mar 08, 2010 | Heating & Cooling
Jan 01, 2010 | Heating & Cooling
811 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: